OutBack FLEXware 500 3.0 Kw Grid-Tie Power Center.
OutBack 3.0 Kw Grid-Tie Power Center Model: OBFW5-GTFX3048S
Continuous AC Power Rating: 3.0 Kw (3,000 watt AC)
Battery Voltage: 48 VDC
AC Output Voltage: 120 VAC/60Hz
Charger Amps: 35 Amps
Inverter(s) Quantity: 1
Fully Assembled and Tested
NEC-compliant assembled power systems include inverter(s), AC enclosure with inverter bypass, DC enclosure, inverter disconnect breaker and shunt, all mounted to a back plate and wired. Charge controllers, battery cables, and displays are not included. Charge controllers, additional AC and DC input and load breakers can be added at the time of assembly, or in the field. Many other options are available. Please contact us for more information. Power systems ship by truck freight. ETL Listed to UL standards.
Grid-Tie FLEXware 500 Systems
Complete one-inverter or two-inverter OutBack grid-tie power systems based on Out-Back FLEXware 500 power system components. Choose a 24V or 48V system, and either the sealed or vented inverter models. Use with one or two FlexMax charge controllers and a solar array to create a fully automated utility-intertie system with battery backup.
Each power panel, in addition to the inverter(s), includes the FLEXware 500 AC and DC enclosure back plate, DC inverter breakers, 120/240 VAC-input-output-bypass breaker assembly, OutBack MATE3, HUB4, AC-DC surge protector, and RTS remote temperature sensor, all installed.
Other options, such as AC and DC circuit breakers, and the FLEXnet battery monitor, can be assembled and tested in our ETL certified shop, or installed in the field. The X-240 auto-transformer can only be installed on single inverter in grid-tie systems for 120/240 VAC output. The X-240 cannot be installed with 2 inverters in grid-tie systems due to anti-island requirements.
These grid-tie power panels are not recommended for use with most engine generators.