Off-grid solar complete power center rated at 3,500 watts AC. Single phase output AC at 120 VAC 60 Hz. Power centers combine your battery charger, fusing, disconnects and inverter output. 3,500 watt AC power center protects your electrical power bus. Solar pv panel and wind generator battery charging can be controlled with this power center. OutBack FLEXware 500- 3.5 Kw Grid-Tie Power Center.
OutBack 3.5 Kw Grid-Tie Power Center Model: OBFW5-GVFX3524S
Continuous AC Power Rating: 3.5 Kw AC
Battery Charging Voltage: 24 VDC
AC Output Voltage: 120 VAC/60Hz
Charger Amps: 55 Amps
Inverter(s) Quantity: 1
Fully Assembled and Tested
NEC-compliant assembled power systems include inverter(s), AC enclosure with inverter bypass, DC enclosure, inverter disconnect breaker and shunt, all mounted to a back plate and wired. Charge controllers, battery cables, and displays are not included. Charge controllers, additional AC and DC input and load breakers can be added at the time of assembly, or in the field. Many other options are available. Please contact us for more information. Power systems ship by truck freight.
Off grid power center ETL Listed to UL standards.
Grid-Tie FLEXware 500 Systems
OutBack assembled, wired and tested, complete one-inverter or two-inverter OutBack grid-tie power systems. Remote solar pv and wind generator based on Out-Back FLEXware 500 power system components.
Choose 24/48 VDC battery charging system. Sealed or vented inverter models. Use with one or two Flex-Max charge controllers and a solar array to create a fully automated utility-intertie system with battery backup.
Each power panel, in addition to the inverter(s), includes the FLEXware 500 AC and DC enclosure back plate, DC inverter breakers, 120/240 VAC-input-output-bypass breaker assembly. Off grid battery charge controller inverter OutBack MATE3, HUB4, AC-DC surge arrester, and RTS remote temperature sensor, all installed.
AC and DC circuit breakers, and the FLEXnet battery monitor, can be assembled and tested ETL certified shop, or installed in the field.
X-240 auto-transformer can only be installed on single inverter in grid-tie systems for 120/240 VAC output. The X-240 cannot be installed with 2 inverters in grid-tie systems due to anti island requirements.
Solar power center Flexware 500 rated at 3,500 watts AC for 24 VDC battery bank.