Solar off-grid battery power center inverter rated at 7,000 watts AC. Single phase AC output at 120/240 VAC 60 Hz. Fully integrated power center. Includes charge controller, battery voltage regulation during charging and discharging, and inverter AC output. OutBack FLEXware 500 - 7.0 Kw Grid-Tie Power Center.
OutBack 7.0 Kw Grid-Tie Power Center Model: OBFW5-GVFX3524D
Continuous AC Power Rating: 7.0 Kw AC
Battery Voltage: 24 VDC
AC Output Voltage: 120/240 VAC/60Hz
Charger Amps: 120 Amps
Inverter(s) Quantity: 2
Fully Assembled and Tested in the factory.
Fully NEC-compliant. Assembled power systems include inverter(s), AC enclosure with inverter bypass, DC enclosure, inverter disconnect breaker and shunt. All mounted to a back plate and wired. Charge controllers, battery cables, and displays are not included. Charge controllers, additional AC and DC input and load breakers can be added at the time of assembly, or in the field.
Off grid solar and wind remote home power center. Control your solar PV battery charging. Battery charging voltage 24 VDC. ETL Listed to UL standards.
Grid-Tie FLEXware 500 Systems
Fully assembled, wired and tested. Complete one-inverter or two-inverter OutBack grid-tie solar and wind power system based on Out-Back FLEXware 500. Choose a 24/48 VDC battery charging system. Choose sealed or vented inverter models. Use with one or two FlexMax charge controllers and a solar array to create a fully automated grid tie system with battery backup.
Each power panel, in addition to the inverter(s), includes the FLEXware 500 AC and DC enclosure back-plate. DC inverter breakers, 120/240 VAC-input-output-bypass breaker assembly, OutBack's MATE3, HUB4, AC-DC surge protector, and RTS remote temperature sensor, all installed.
Other options, such as AC and DC circuit breakers, and the FLEXnet battery monitor, can be assembled and tested in our ETL certified shop, or installed in the field.
Off-grid X-240 auto-transformer can only installed on single inverter in grid-tie systems for 120/240 VAC output. Note: X-240 cannot be installed with 2 inverters in grid-tie systems due to anti-island requirements.
Solar and wind off grid power center 7,000 watts AC. Single phase 120/240 VAC 60 Hz. Battery charging voltage 24 VDC. Use solar pv panels and wind generators to charge your 24 VDC battery bank. Of-grid solar OutBack power centers have integrated the power control.
Remote home power systems for solar PV and wind generator battery charging with inverter AC output 7 Kw AC.