Large power center rated at 7,200 watts AC. Off grid solar PV and wind generator battery charging power center. Battery charing voltage 48 VDC. Use solar PV panels and wind generators to charge 48 VDC battery banks. Off grid power center OutBack FLEXware 500 - 7.2 Kw Grid-Tie Power Center.
OutBack 7.2 Kw Grid-Tie Power Center Model: OBFW5-GVFX3648D
Continuous AC Power Rating: 7.2 Kw AC
Battery Voltage: 48 VDC
AC Output Voltage: 120/240 VAC/60Hz
Charger Amps: 40 Amps
Inverter(s) Quantity: 2
Fully Assembled and Tested
Solar off grid power center is NEC compliant. Factory assembled power center systems include inverter(s), AC enclosure with inverter bypass, DC enclosure, inverter disconnect breaker and shunt. Mounted to a back plate and wired.
REC Solar PV panels 250 watts 24 VDC wired in series for 48 VDC battery charging. Battery charging up to 40 Amps.
Off grid wind generator and solar charge-controllers, battery cables, and displays are not included. Charge controllers, additional AC and DC input and load breakers can be added at the time of assembly, or in the field. Many other options are available. Please contact us for more information. Power systems ship by truck freight. ETL Listed to UL standards.
Grid-Tie FLEXware 500 System features:
Factory assembled, wired and tested. Complete off grid one-inverter or two-inverter OutBack grid-tie power systems based on Out-Back FLEXware 500. Select 24/48VDC battery charging system. Select sealed or vented inverter models. Use with one or two FlexMax charge controllers and a solar array to create a fully automated net metering system with battery-backup for emergencies.
Solar and wind off grid inverter(s), include the FLEXware 500 AC and DC enclosure back plate. System includes DC inverter breakers, 120/240 VAC-input-output-bypass breaker assembly, OutBack MATE3, HUB4, AC-DC surge arrestor, and RTS remote temperature sensor, all factory integrated.
Off grid power center AC and DC circuit breakers, FLEXnet battery monitor, can be assembled and tested in OutBack ETL certified shop. Off grid X-240 auto-transformer can only be installed on single inverter in grid-tie systems for 120/240 VAC output. The X-240 cannot be installed with 2 inverters in grid-tie systems due to anti-island effects.
Off grid solar and wind power center for 7,200 watts AC output. Battery charging voltage 48 VDC. Use solar PV modules and wind generators to charge your 48 VDC battery bank.
Whisper 100 rated at 900 watts charges batteries at 48 VDC. REC Solar 250 watt 24 VDC panels wired in series to charge 48 VDC batteries.